First, the indoor unit installation location of choice:
(1) Choose strong, less susceptible to vibration, enough
to withstand the weight of the local unit.
(2) choose not to close to heat, steam source, not into
the unit, where the wind generated obstacles
(3) Select the drain easily, can be connected to the
outdoor unit where pipe
(4) Select cold or hot air can be sent to every corner of
the room where
(5) should choose a place near the air conditioner
outlet, and the machine leaving enough space around
(6) below the indoor unit should be selected without TV,
radio, radio equipment and valuables from the fluorescent lamp 1 m above
(7) in the wall to install the remote control, make sure
the indoor unit in the case of fluorescent lights, can receive signals.
(8) installed in the bedroom, not easy to let the wind
Second, the choice of the outdoor unit installation location:
(1) to withstand the weight of the machine does not
produce much vibration and noise of the place.
(2) a well-ventilated place, wind and exhaust noise does
not affect the neighbours
(3) try to select less susceptible to rain or direct
sunlight and wind blowing the place to be
(4) to avoid the stagnation that may occur and corrosive
gases (sulfur- dioxide, etc.), combustible gas (thinner, gasoline, etc.)
and oil mist spray, steam and more places (for example: the kitchen.)
(5) should allow sufficient space for the benefit of
units out of the wind
(6) should be easy to repair
(7) air conditioner can not be installed in a
non-specific metal structure (such as: security network)
(8) outside the machine to install the street not less
than 2.5 m
(9) Outdoor outlet from the neighbours should not be less
than 3 meters, if necessary, to reach agreement with the neighbours.
Third, the air-conditioning control box check the packing list, complete
inventory of accessories are:
1) indoor and outdoor air conditioning unit out of the
box, check box appearance is in good condition without damage, bandage
tape, sealing tape strapping sealed well.
2) Check the model number on the package air conditioner
and purchase invoices are consistent
3) out of the box, check the availability of indoor and
outdoor unit surface scratches, broken phenomenon.
conditioning packing list, complete inventory of accessories are:
(1) hanging Random annex are: (1) remote control; (2)
Battery 2; (3) wall panels; (4) drain; (5) Cement pin 4; (6) Nursing
ring; (7) connecting pipe; (8) with machine lines; (9) drainage elbow;
(10) damping pads;
(2) Random accessories cabinet are: (1) remote control;
(2) Battery 2; (3) wall panels; (4) drain; (5) Cement pin 4; (6) Nursing
circle 2; (7) connecting pipe; (8) with machine lines; (9) drainage
elbow; (10) damping pads; (11) heat pipe; (12) line bundle; (13)
Fifth, check the meter, power supply, power supply wire,
switches, sockets compliance requirements:
Check the meter:
1) air conditioner consumes 2,200 watts of power; select
the current capacity of the meter 5A (amps) or more assured security;
2) air conditioner consumes 4,400 watts of power in;
select the current capacity of the meter 10A (amps) or more assured
3) The air conditioner power consumption at 6600 W;
select the current capacity of the meter 15A (amps) or more assured
Check the power supply voltage:
1) single-phase power: air conditioning using
single-phase AC power supply: AC 220 V; air conditioning use the normal
power supply voltage range: AC 220 V ± 10% (ie: 198 V -242 V).
2) three-phase power: air conditioning, three phase AC
power supply: AC 380 V; air conditioning use the normal power supply
voltage range: AC 380 V ± 10% (ie: 342 V -418 V).
Check the power wire:
1) a -1.5 horsepower air-conditioning power cord should
be greater than cross-sectional area: 2.5 square millimeters copper;
2) 1.6 -2.5 horsepower air-conditioning power cord should
be greater than cross-sectional area: 4.0 square millimeters copper;
3) 2.6 -3 horsepower air-conditioning power cord should
be greater than cross-sectional area: 6.0 square millimeters copper;
(4) Check the power switch:
1) a -1.5 horsepower air-conditioning power switch should
be greater than: 10 amps or more;
2) 1.6 -2.5 horsepower air-conditioning power switch
should be greater than: more than 20 amps;
3) 2.6 -3 horsepower horsepower air-conditioning power
switch should be greater than 25-30 amp;
(5) Check the power outlet:
1) a -1.5 piece should be larger than air-conditioning
outlet: 10 amps or more;
2) 1.6 -2.5 horsepower air-conditioning outlet should be
larger than: 15 A or more;
3) 2.6 -3 horsepower air-conditioning power outlet should
be larger than 16-30 amps or more;
Security Note: In accordance with the national
air-conditioning products manufacturing and quality certification
standards, as tank machine power, current, therefore, should use the
power switch to control air conditioning power lines to ensure the
safety of the normal air conditioning use.
with air-conditioning power requirements:
1) The use of single-phase power voltage supply of air
conditioners: power supply voltage should be 220 volts AC;
2) be equipped with dedicated power lines, access to
electrical by a qualified staff, according to national standards for
3) The power outlet should be equipped with easy plug-in
air conditioner where the power cord. And must be equipped with ground.
To ensure the air conditioner through the power outlet ground.
Three-wire outlet, ground and neutral must be strictly separated from
the zero line will be connected together with the ground is wrong, the
power plug and power outlet in the correct wiring methods and
requirements, L logo should be connected to the line of fire; N logo
should connected to the zero line; 〨 identity should be connected to the
grounding line; and must be connected.
Check air-conditioning test run articles
Six, air conditioning, air conditioning is normal test
(1) air conditioning and heating effects of the test
methods and requirements:
1) air-conditioning switched on more than 30 minutes, set
the high-speed indoor unit wind speed, temperature meter temperature
probe into the air from the indoor unit 3-5 cm; data stable reading
record.And then the temperature probe thermometer indoor unit outlet
from 3-5 cm, the data stable reading record.
2) indoor air inlet and outlet temperature difference
between the test data standards:
Hanging Machine: refrigerating operation ,10-12 degrees;
heating operation ,18-25 degrees;
Cabinet Machine: refrigerating operation, 11 degrees ± 2
degrees; heating run, 18 degrees ± 2 degrees;
(2) the noise when the air conditioning inspection
1) indoor and outdoor unit should be installed should be
the level of solid, hanging wall board machine should be fixed firmly,
the outdoor unit should be firmly fixed cabinet machine corner screws
2) The indoor unit can be run to configure the remote
observation of the different wind speed changes, carefully monitor the
abnormal sound or no other foreign body within the indoor unit friction
3) The outdoor unit should be the normal operation of the
compressor and outdoor fan sound, inverter air conditioner running in
the high-frequency sound is slightly larger operation is normal.
Air-conditioning operation using the attention points:
(1) the use of air conditioning operation when the
recommended temperature setting reasonable parameters:
Reasonable and comfortable indoor environment control the
temperature of 22-28 degrees Celsius
(2) the use of air conditioning operation when the
heating temperature setting recommended reasonable parameters:
Reasonable and comfortable indoor environment control
temperature 18-22 degrees Celsius
(3) Operation air conditioning or dehumidification
When the ambient humidity, the cooling or dehumidifying
operation mode, the outlet may drip, because indoor air outlet louvers
of the large temperature difference between inside and outside the
normal result of condensation.
(4) Air Conditioning healthy operating conditions:
When the indoor unit is running (normal state) and the
health of key press to the healthy operation of the
(5) inverter air conditioner inverter control:
Inverter air conditioner starts, that is automatically
run, quick to reach temperature. Reaches the set temperature,
automatically using low-power operation or shutdown.
(6) Air Conditioning 3 minutes protection function:
If, after re-boot immediately after shutdown, the
compressor takes 3 minutes to start to protect the machine
(7) Air Conditioner wind speed changes:
1) In cooling mode, air is set to automatic mode at room
temperature, wind speed near the set temperature automatically reduced.
3) In the dehumidification mode automatically changes
speed indoor unit.
(8) to prevent cold air blowing: (single cold models such
Air conditioning and heating operation, indoor fan does
not start immediately after the rotation to prevent cold air blowing.
(9) defrost function: (single cold models such function)
1) In heating operation, when there is frost on the
outdoor unit heat exchanger formed, the air conditioning will
automatically defrost a few minutes.
2) The indoor unit during defrost fan not running. After
defrost, air conditioning will automatically resume operation.
(10) when the air conditioning system for the love of hot
Heating air conditioner when the draw heat from the
outside and released into the room, so the level of the outdoor ambient
temperature will affect the heating effect.
(11) Air Conditioner auxiliary heating conditions: (with
auxiliary heating model)
Allowed to set conditions of electric heating, air
conditioner microcomputer control the indoor temperature is less than 23
degrees Celsius detected, below the set temperature, and the difference
with the set temperature more than 2 degrees Celsius, the auxiliary
heating in operation, otherwise, automatically stops auxiliary heating.
(12) air conditioning by remote control:
1) signal transmission when used to align the indoor unit
on the head signal reception window.
2) The signal transmission between the head and the
window should normally be received within 7 meters, and not due
3) Do not throw the remote control bump
4) with an electronic start-type fluorescent lamps,
fluorescent lamps or cordless phones convert the room, the signal
receiver window of the received signal will be affected by interference,
when used as long as the distance closer to the indoor unit.
Safe use of air conditioning articles
(13) air safety and precautions to use:
1) air-conditioning when not in use for a long time,
please cut off air conditioners power.
2) air conditioner outlet or switch must be configured
with ground to ensure the safe use of air conditioners to avoid the
danger of electric shock!
3) Use capacity of the fuse or switch. To achieve the
proper protection of human and machine.
4) Do not install the air conditioner near flammable gas
leak prone areas, in order to avoid gas leak caused a fire.
5) Do not ground the air conditioner connected to the gas
pipe, water pipe, lightning rod, telephone land line
6) Do not use water or dripping air conditioners and
parts cleaning cloth to avoid damage to air conditioning.
7) Clean the indoor unit filter network on a regular
basis, so as not to influence the effect of air-conditioning,
air-conditioning power consumption to increase, causing failure.
8) For indoor and outdoor unit air inlet and outlet to
keep open. To ensure that the effect of air-conditioning
(14) Air conditioning installation or removal machine
1) The user unit air conditioner is installed or removed,
should be through the professional manufacturer of air-conditioner-site
installation service staff.
2) If the user-machine air conditioner installed or
removed, you must have a professional installation tools and
professional operation of technical skills, in strict accordance with
product instructions in the installation setup requirements by
installing technology installation or transfer machine.
(15) air conditioner repair and maintenance requirements:
Including repair policy: 2008 to buy Haier Air
1) The machine and its six key components for repair,
compressor repair kits six years, the other in accordance with the
"provisions of the new national three guarantees" for processing.
2) Key components include: indoor and outdoor unit PC
board, indoor and outdoor electrical and mechanical machines, indoor and
outdoor unit sensor, four-way valve, evaporator, condenser, indoor and
outdoor unit piping system components (excluding the tube is connected
both inside and outside), indoor and outdoor unit control board (LCD
1) filter dust, drainage, refrigerant leaks, loosen
machine, check the pipe wrap, wall hole.
(16) How many degrees below the outdoor temperature when
the air conditioning effect will be affected?
1) fixed-frequency heating and air conditioning in the
outdoor temperature is below normal minus 7 degrees Celsius, more than
the normal use of air conditioners and heating effect will be affected.
2) fixed-frequency heating and auxiliary heating air
conditioning is generally lower than minus 9 degrees Celsius outside
temperature is below, more than the normal use of air conditioners and
heating effect will be affected.
3) the general frequency heating and air conditioning in
the outdoor temperature is below minus 15 degrees Celsius, more than the
normal use of air conditioners and heating temperature effect will be
(17) household electrical appliances with a nominal value
of the actual power consumption differences:
1) air conditioner and the actual technical performance
parameters are different, specifically reflected in the outdoor unit,
because the working temperature of the outdoor unit (technical term:
working conditions), with the outdoor temperature of its operating
current, cooling pressure, compressor power will change, so the
technical parameters of the outdoor unit on the nominal value, specify
the maximum technical parameters. (With the indoor unit or the manual a
bit different, which is required by industry standards)
Product maintenance articles:
(1) indoor unit hanging unit filter network regularly
cleaning and maintenance requirements and steps:
1) The indoor unit cleaned once every two weeks check the
filter net, do not use hot water above 40 degrees filter net, filter net
or cause deformation.
2) Turn off the air conditioner power supply, open the
gate into the wind: the right to use the machine into the grille into
the grille from the roof support.
3) Remove the filter network: Gently push up the filter
network center processes, and then pull down
4) Install the air filter: The air filter box around
embedded filter network.
5) Install the air filter net: (be sure to install)
installation, the multi photocatalyst, embedded in the left box, air
filter, air filter media embedded in a strong bactericidal right box.
6) Close the inlet gate: the gate into the wind down the
roof, close the gate into the wind.
Indoor Rack unit filter network of regular cleaning and maintenance
requirements and steps:
1) The indoor unit inlet gate keeping guard at both sides
of the upper hand, gently pull out after the force, then you can lift.
2) into the indoor unit's air up and out of the gate by
3) The indoor unit cleaned once every two weeks check the
filter net, filter net clean indoor unit is not greater than 40 degrees
with hot water, it will filter into the net after the moisture to dry
indoor air into the gate and then into the indoor unit in which be.
(3) outdoor cleaning and maintenance requirements:
1) The outdoor unit's heat exchanger on the air if there
too many foreign objects or dust on the surface should be promptly
cleaned with a brush. To ensure the air conditioning compressor is not
2) prior to use air-conditioning season, check the air
conditioning full power supply is normal, (a long time without air
conditioning power supply should be cut off) Check the outdoor unit if
the dust cover should be removed.
3) after the air conditioning is not used before the
season, indoor and outdoor air-conditioning unit cool and dry with a
cloth to wipe after, (a long time without air conditioning power supply
should be cut off) to the outdoor unit stamped dust cover.
Second, use of air conditioning and consultation to
answer frequently asked questions:
(1) Air conditioning smell:
Use of air conditioning in the summer, in the
just-machine or shutdown, the machine may be the phenomenon of blow odor.
This is because when using the cooling function, the evaporator
condensate prone, adhesion of the dust in the air, resulting in a moldy,
the air smell. At this time, attention should be turned off before each
set to air conditioning mode (or higher temperature settings), so air
conditioning to work for 3-5 minutes, the surface of the condensate
evaporator drying on it. Air conditioning heating in the winter, when we
use the air conditioner will have some odor, or no light in the summer,
this is normal.
Heating in the winter when the air-conditioning, if any
odor phenomenon, please note the following when used:
1) If the number of normal filter cleaning smoke less or
more rooms, the odor filter network will increase
2) In daily use, as long as the time to clean the filter
(usually cleaned once every two weeks) or in the indoor spraying of some
of the inlet air freshener, that is,
Reduce this phenomenon.
(2) air conditioning condensation within the machine
Air conditioning in the refrigeration, condensation phenomena inside the
machine window has the following reasons:
1) remote control set temperature is low;
2) The ambient air humidity;
3) low-speed indoor speed settings;
4) the angle of the louvers to adjust properly for a long
time down wind or down swings, the louvers of the large temperature
difference between inside and outside, resulting in condensation
If the above phenomenon, please adjust the set
temperature, the temperature below 5 degrees below, if your indoor
humidity is high, set in the dehumidifying air-conditioning settings,
such as do not have this feature, you need to maintain ventilation;
Please set the same speed, high wind speed can reduce the condensation
Air conditioning unit has dark spots within:
Anion air-conditioner used for a period of time, the
machine inside the machine near the surface and the walls are dark spots
appear, this is due to adsorption of negative ions in the environment
with the function of bacteria in dust, smoke, bacteria attached to the
filter network and on the ground, with a small amount of In the case of
metal surface, for a long time will have visible mold, but this is not a
failure, but not moldy.Therefore, please note that regular cleaning of
the outer surface of the air conditioner, clean the filter to clean and
maintain the cleanliness of indoor air, pay attention to ventilation can
often avoid this phenomenon.
sound expansion and contraction:
Air-conditioning inside the machine run-time issue, "A
pair of clap" sound is due to thermal expansion and contraction caused
by plastic, this is not malfunction. Such as televisions and other
plastic changes in the structure and the internal temperature of
electrical appliances will have this phenomenon.
As air inside and outside the large temperature
difference, according to the principle of thermal expansion and
contraction will cause a slight plastic issued "A pair of clap" sound,
and that the better air-conditioning, air conditioning, the temperature
difference between inside and outside the greater, the plastic
deformation of the more obvious, so "A pair of clap" sound is also
The cooling effect is not good:
If the air conditioning work, but feel inadequate, please
check whether it is the following:
1) whether the regulation in accordance with the
requirements of operating the controller, set the temperature and wind
speed is appropriate: the right temperature 22-28 degrees Celsius, wind
speed, wind speed or low speed settings.
2) whether the dirty filter mesh: filter cleaned once
every two weeks
3) there is an obstacle in and out of air: the air inlet
and outlet that can not be placed item, affect the air-conditioning
4) Indoor has other sources of heat, or the room a lot of
people: the need to remove the heat
5) room with glass walls, indoor and outdoor heat
(6) The heating effect is not good:
If the air conditioning works but it feels hot enough, please check
whether it is the following:
1) whether the adjustment operation of the controller as
required, set the temperature and wind speed is appropriate: the right
temperature 18-22 degrees Celsius, wind speed and set the stroke
2) whether the dirty filter mesh: filter cleaned once
every two weeks
3) There is an obstacle in and out of outlet
4) The reason the ambient temperature is too low (the
temperature falls below -5 ℃ below): the normal use of heating and air
conditioning ranges from -5 ℃ to +43 ℃, heating time, absorb heat from
the outside, and then sent to the room, when the outdoor temperature
very low, the absorption of heat is very limited, resulting in poor
indoor heating effect.
5) room with glass walls, indoor and outdoor heat
6) Check the power voltage is too low: below the supply
voltage less than 187V, air conditioning does not work or performance
air conditioner shut down frequently:
Air conditioner stop frequent reasons are:
1) the temperature set temperature and room temperature
is too small;
2) air conditioner, the wind outside the machine around
3) Room insulation effect.
For the above reasons is caused by frequent stops to open
the reason, it is because when the indoor temperature and set
temperature and the temperature difference between the outdoor ambient
temperature close to when this phenomenon is normal. At this point you
according to the required temperature, on the remote control to set the
appropriate increase or decrease the temperature 3-5 degrees, to reduce
the open air park frequent phenomenon.
Air conditioning voltage scope:
Fixed-frequency air-conditioning operation, the power
supply voltage range is 198-242 volts, lower than 187 volts or less will
not start. Inverter air conditioner operation, the power supply voltage
range is 198-242 volt, 150 volt inverter air conditioner can be started
when the ultra-low voltage, but not to normal operation (variable
frequency drive for variable frequency operation, power, current become
larger, the power supply due to too low results in low voltage
protection does not work)
(9) The air conditioner does not start:
Air conditioning does not start when you check the
1) Power has power, whether the power failure;
2) Power plug is a good contact;
3) Remote control battery has power, such as lack of
electricity, transmission signal is weak, the indoor unit does not
4) remote control distance is too large, the signal
attenuation is more severe, the indoor receiver to receive bad.
1) Check whether the power supply voltage between 198-242
2), re-off power after 3 minutes and then test machine;
3), replace the remote control batteries.
(10) the use of remote control distance:
Air conditioner remote control use of distance, the
signal transmission when used on the indoor unit head aligned signal
reception window. Signal transmission between the head and the receiver
window (typically 30-60 degrees horizontal angle) in the 7 m distance
within the air-conditioner remote control, and not due to obstructions
to the normal reception of the work (the remote control The battery must
ensure that the capacity of normal)
Note: start with e-type fluorescent lamps, fluorescent
lamps or cordless phones convert the room, the signal receiver window to
receive the signal susceptible to interference, the use of distance as
long as the remote control closer to the indoor unit.
How long time do not air conditioner maintenance:
1) do not have air conditioners in a long time (seasonal
store) placed before the maintenance, in the sunny air condition, power
running about half a day, the air conditioning inside completely dry.
2) Turn off the air conditioner's power, or even if the
air conditioner is stopped, will consume some power.
3) clean the filter, loosen with a cloth indoor, outdoor
dust cover, conditions can cover the outdoor unit housing units.
4) for a long time do not remove the batteries when the
remote control, remove the battery if any appear, click on spikes with a
Air conditioners in what circumstances need to add refrigerant
1) air conditioner installed in the normal air
temperature range (-7 degrees to 43 degrees), the normal effect of
cooling and heating, (air conditioner refrigerant refrigeration system
does not leak) refrigerants do not need to fill on a regular basis, if
the use of air conditioning in the normal sense of the temperature range
is not effective. Contact with manufacturers of home maintenance service
to maintain the remote control:
1) air-conditioning for a long time do not use the remote
control's batteries should be removed to avoid battery leakage and
corrosion of components within the broken remote control.
2) Use good quality batteries to avoid battery leakage
and corrosion broken remote control.
3) placed in remote areas away from the sun.
4) The remote control can not have items on top of the
5) Avoid the remote control erosion of the surface to oil
6) Do not throw bump the remote control.
To retain maintenance records user certificate:
1) The user will save the purchase invoice and warranty
card is good, and every single take good care of the maintenance of
records, users can maintain detailed records of records as a single
package, the package, the warranty certificate to enjoy the national
three guarantees of effective law regulations.
(15) home air conditioning warranty policy:
1) Since January 1, 1996 to July 1, 1998 to purchase the
air conditioner; requirements: 1 year machine repair kits extended to 18
months, 3 years compressor repair kits extended to 5 years, the main
components repair kits for 3 years.
2) Since July 1, 1998 after the purchase of air
conditioners; requirements: 6 years compressor repair kits, machine
repair kits 3 years.
Since January 1, 2008 after the purchase of air
conditioners; requirements: press for repair 6 years, the whole package
repair 6 years.
Haier, Mitsubishi Heavy Industries press for repair 3
years, 3 years of machine repair kits.
3) The main parts include: internal and external computer
boards, internal and external mechanical and electrical machines, inside
and outside temperature sensor, four-way valve, evaporator, condenser,
piping system components inside and outside the machine (excluding the
tube is connected both inside and outside), inside and outside the
master panel (liquid crystal display panel).